|Designed for whole house disinfection at point of entry, the 3MUV-8 doses incoming water with 40mj/cm2 at 8 gpm ensuring your water remains potable once it enters your home or cottage. A compact mounting footprint ensures ease of installation.|
Lamp change timer reminder: every year. Bulb = $99
Compact Size For Easy Installation: Size = 48 x 10 x 15 cm (18 x 4 x 6" )
Audible Lamp Failure = yes
Max: 10 Gallons Per Minute
Rated: 8 Gallons Per Minute
Average House In City and Cottage is only 5-7 Gallons Per Minute, Therefore, this 3M unit is perfect to ensure maximum protection for your drinking water.
Replacing the Lamp & Cleaning
To replace the lamp:
1) Disconnect from power source. Disconnect the lamp
connector from the UV system by carefully separating it from the gland
nut (use the aid of a slot screwdriver if required).
2) Disconnect lamp connector from lamp and carefully
remove the UV lamp.
3) Replace the new lamp being careful not to touch the
new UV lamp "glass" with your fingers as oils impair UV transmission. If
contact does occur, clean with alcohol and reconnect carefully replacing
lamp into stainless steel disinfection chamber.
4) press lamp connector into aluminum gland nut.
5) plug power source into outlet. Verify "POWER-ON"
LED is illuminated and ballast audible start-up sequence operates.
Reset when UV Power Source is in
Annual Alarm Mode
To reset the UV power source when the red timer LED
light is either flashing or fully on, hold down the timer button while
connecting the UV power source to the AC supply voltage. Continue
holding the button until the UV power source emits a continuous three
second beep indicating that the lamp timer has been reset.
Reset when UV Power Source is not in
Annual Alarm Mode
It is not possible to reset the timer using the above
procedure if the annual lamp change reminder timer has not activated as
indicated by either the flashing or solid red timer LeD light. To enable
timer reset, operate the UV power source with no lamp connected until it
enters the lamp failure state as indicated by the audio alarm beeping
and the lamp and timer LED lights shutting off. Disconnect from AC
supply voltage, replace the UV lamp and proceed as above.
Verifying Timer Reset
A timer reset can be verified by pressing the timer
button once and counting the flashes of the red timer LeD light. The
timer LeD will flash once for each month of lamp life remaining. This
feature can be used at any time to determine the months of lamp life